Yes, however it must be sleeved in a non-metallic conduit ½” larger than the pipe. The underground section must not contain a fitting.
HOME-FLEX CSST has been tested and certified by CSA and IAPMO for compliance with the industry standard ANSI LC-1 / CSA 6.26, “Fuel Gas Piping Systems using Corrugated Stainless Steel Tubing (CSST).”
Home-Flex® CSST and Underground products meet all necessary requirements, but check your local codes prior to purchase and installation.
80% lighter, 70% faster (no cutting and threading of pipe) 50% labor saving.
If it is a fixed appliance, yes. If not, we recommend terminating the HOME-FLEX pipe and attaching a gas connector.
Yes, HOME-FLEX (previously name alpha-flex) will only work with HOME-FLEX, or alpha-flex, tubing and fittings.
Thoroughly read the Home-Flex® Underground and CSST Design & Installation Manuals available in the “Resource” section of this website. Then use the “get certified” button on the site to answer a few basic questions. You will be emailed a pdf version of your certification card for use with inspectors if required.
No, but you do need to be certified to install Home-Flex CSST.
No, we’re a distributor only and are not set up for direct consumer purchases